1800 800 878
Time for serviceMorningAfternoonOutside business hours
By submitting this request, you agree to our Terms and that you have read our Data Use Policy.
Book NowPlease leave this field empty.
Please select...ACTNSWNTQLDSAVICTASWAOutside Australia
Send EnquiryPlease leave this field empty.
If your compressor is installed in a small enclosure, it will benefit from ducting the hot air out of the enclosure. The ductwork cross section should be at least as large as the cooler. It does not need to be anything fancy or factory made.
Whether it’s made from sheet metal, self-tapping screws and duct tape or plywood with hinged doors, anything that ducts the heat out of the room will do, but remember to leave a door to reach and clean the coolers.
Did you know unenclosed compressors need ventilation too? Cross flow is always best with an exhaust fan and louvred hot air discharge near the top of the room. Remember to size the vent at least as large as the cooler, and the vent fan should displace more cfm than the compressor’s cooling fan. Cooling fan cfm ratings can be found in the specifications for most air cooled rotary screw compressors.
Paying close attention to the operating temperatures of your rotary screw compressors and protecting them from the summer’s heat will extend the life of your air compressors and your oil.
If you have any queries or would like us to inspect your compressor, we welcome you to contact us!
Copyright © 2015 CAPS Australia
Chromatix Web Design Melbourne